I found some gap (19 mils = 0.49 mm) on one foot of Steam Condensing Turbine.
the reading was taken in cold condition,
the question are:
how much is permissible for this kind of gap?
this gap is for bad installation (soft foot) or gap for thermal expansion?
what is the cause of this kind of gap?
I appreciate your comments.