A centrifugal pump increased his vibration amplitude
Pump: Centrifugal | 1 stage | DE BRG 6308EN | NDE 6308E
Motor: 4 poles | 480V
PeakVue analysis (2KHz, Fmax=4xBPFI, 120lbf flat rare earth magnet) suggest possible outer race damage. (BPFO = 3.08X)
During overhaul, misalignment and outer race damage were found
The equipment probably suffered a blow or fall during transportation or installation, damaging the bearing.