I am seeing 300 Hz in the spectrum on an 50 Hz LF AC motor with soft starter. I'm suspecting it is from SCR Firing rate but would it be possible to have SCR on an AC motor? Hoping to hear from the expert on this topic
Thanks for the reply. Yes the motor has no VFD only soft start AC motor. However, I am confused because I read some articles that says SCR can also be used both for AC and DC motors. If I may calculate the peak frequency of interest for the sake of representation it coincides with the full-wave rectified 6 SCR circuit on a 50 HZ LF. It may not pose a potential problem but it's good to know from my perspective when troubleshooting Electric motors. I am not an electrical guy but really keen to learn from the experts.
Soft starters are also known as reduced voltage soft starters (RVSS). A soft starter relies on three pairs of SCRs (silicon controlled rectifiers) — one pair for each phase of power — that are applied gradually for portion of each voltage phase, limiting the voltage provided to the motor.21/11/2018
Some soft starters keep the SCR's in the circuit at all times. Some utilize a start/run contactor dropping the SCR's out after startup. Yours may keep the SCR's in the circuit at all times and yes you are correct full wave rectified with 6x50Hz SCR's=300Hz or 18,000 cpm exactly. I see in your plot a small peak to the left of SCR frequency, I assume that is 4x run speed?
As a rule of thumb I have used .1 in/sec/pk to fix or trend, I believe this same value is acceptable for DC or AC motors. Others on this site may have more knowledge than myself regarding these values.
Have seen soft foot on motor cause 2xLF to increase. If you have the ability to monitor motor live time, loosen one motor foot at a time and watch to see if 2xLF decreases.
Thanks Dave at least I can now confirm that SCR is also present in AC motor depending on what system you're using and what for. The small peak on the left of SCR is the 6x RPM. The motor is running 1500 RPM. You're right, I am suspecting also airgap dissymmetry caused by soft foot, unfortunately the company is hesitant to do what you've suggested. Since the amplitude level is still very low ~0.7 mm/sec I don't think I will make a call.
When you block a person, they can no longer invite you to a private message or post to your profile wall. Replies and comments they make will be collapsed/hidden by default. Finally, you'll never receive email notifications about content they create or likes they designate for your content.
Note: if you proceed, you will no longer be following .